Here are some photos of the bursted GRP pipe which was filled with about 2m overburden soil.
The penstock data are:
Discharge =3.2 m3/s
The main reason for the burst was the movement of pipe alignment due to landslide.
|The hole in ground made by the brusted pipe.|
Coupling for GRP
Hard stone lining in inlet canal